ADEMCO VISTA 128BP INSTALLATION MANUAL PDF
View and Download Honeywell VISTABP installation and setup manual online. Commercial Burglary Partitioned Security Systems. VISTABP Security. Index of /manuals/Ademco/Control Panels/Vista VistaBP · VistaBP v1 Installation · VistaBP v1 Program Congratulations on your ownership of an ADEMCO Partitioned Security. System. You’ve Panel Linking networks up to eight VISTABP/VISTABP control panels .. At the time of installation, you were assigned an authority level and a.
|Published (Last):||3 October 2018|
|PDF File Size:||7.76 Mb|
|ePub File Size:||14.3 Mb|
|Price:||Free* [*Free Regsitration Required]|
Partitioning and Panel Linking Table of Contents Programming for TeleSmart It is a single-door access control module.
Index of /manuals/Ademco/Control Panels/Vista-128
This allows the installer to program the download phone number, subscriber number, and primary central installationn receiver phone number without entering the normal program mode.
Setting this field to 1 for a specific partition causes that partition to affect the operation of the mznual User Access Codesthe keypad programmed to arm or disarm the lobby.
Trouble sounds rapid beeping Therefore, panics must be programmed for Partition 1. Enter the panel ID number of the panel you want to link to. Enter the partition number of the panel.
Mounting the Control Cabinet To wire the alarm output using the supervision To access the application note: A short on the polling loop is indicated by a trouble on Step Installagion zone and reports as a trouble condition only.
If Select devices from the list of compatible annunciation is desired, program the zone as type The reception is supervised for two conditions: Connect the negative side of the smoke detectors to terminal 7 of the control.
Green LED Orange a.
All ground leads to terminals 2, 5, and 9. See Figure for the proper Figure Connect keypad wiring as shown in Figure see the chart below for the maximum wire run length for wire gauge you are using.
If the system hangs up the phone line when calling in from a remote location, check the phone connection terminals Term. The This product instaloation the transformer CN in total current drawn from the alarm output may be up Canada.
If you are using X devices, the X10 to 1. Available from 3- in this product to be effective, the designated earth prong, VAC, power outlets only. Calculate alarm currents, then add to get all listed outputs from Tables 1 through 3, then the Alarm Output current subtotal. Alarm Output Current Load Table 4: The standby battery is automatically tested for Table 6: Battery Selection Table 10 minutes every 4 hours, beginning 4 hours Section 4 — Programming Below is a list of the main menus.
Interior, Follower the way in which the system responds to faults in that Provides a delayed alarm using the programmed entry zone.
To program for ACS zone inputs, perform the following steps Enter the partition number Alone Access Control Enter the input type: A user can trigger an access point i.
This restarts the exit delay. The system automatically resets the specific shutdown for a zone after 48 hours if there are no trips on any zone. Cross a fire zone with another fire zone only, and BOTH must be protecting the same physical area no walls or partitions separating them. Consult NFPA 72 standard for exact spacing requirements. Only one of the options may be active within the system.
Zone 5 cannot be used as protection zone. Each schedule consists of one time window programmed using the Time-Driven Event for openings and one time window for closings.
Refer to Timed Events? Time-Driven Event Programming later in this section for detailed procedures. Temporary The following worksheet is an example of the schedules are programmed separately, using the 81 worksheet found in the Programming Guide.
Auto bypass — Zone list Zone list Enter the code for the desired action and Auto unbypass — A user action is to take place. Enter the relay group number. Enter 0 to select all partitions. The holidays used for the access groups are the same as those defined in the holiday schedule. The output devices themselves are programmed into the system by the installer during Output Programming in the 93 Menu Mode.
The end user needs only to know the output device number and its alpha descriptor. Section 7 — Downloading Getting On-Line with a Control Panel At the protected premises, the control panel must be To download a control without programming any connected to the existing telephone line refer to information, perform the following steps: No programming Step Action of the panel is required before downloading to an Step Action Step Action Check the keypad-initiated alarms, if Notify the central station that a test of the programmed, by pressing the panic key pairs system is being performed.
Zone operating on battery power only. The control cabinet must be protected from unauthorized access.
This equipment has been tested and found to comply with the limits for a Class B digital device, pursuant to part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference in a residential installation. Data to control panel B-2 Pager 1 Delay Index Restore Report Timing Connection of any device s to a communicating bus of a Honeywell security system e.
Page of Go. Partitioning and Panel Linkin Page 23 – Figure Page 24 – Figure Wiring a PRM using a Page 26 – Figure Polling Loop Connections to Installing the ENHC wit Page 31 – Figure ivsta Page – Changing a Master, Manager, or Operator Table of Contents Add to my manuals Add.
Commercial burglary partitioned security system with scheduling pages. Commercial burglary partitioned security system with scheduling 88 pages. Commercial fire and burglary partitioned security system with scheduling pages. List Of Figures Figure Panel Linking Trouble sounds rapid beeping Therefore, addmco must be programmed for Partition 1.
Smoke Detector Reset Connect the negative side of the smoke detectors to terminal 7 of the control. Power – Page Page 75 Only one of the options may be active within the system.
Getting On-line With A Control Panel Section 7 — Kanual Getting On-Line with a Control Panel At the protected premises, the control panel must be To download a control without programming any connected to the mnual telephone line refer to information, perform the following steps: Regulatory Agency Statements The control cabinet must be protected from unauthorized access.
Page Index Restore Report Timing Page Honeywell factory service. This manual also for: Comments to this Manuals Your Name.
HONEYWELL VISTABP INSTALLATION AND SETUP MANUAL Pdf Download.
Enter text from picture: By pressing ‘print’ button you will print only current page. To print the manual completely, please, download it. Don’t show me this message again. Got it, continue to print. Don’t have an account?